HORIZONTAL TYPE CONDENSING UNIT is characterized by its compact structure, small size, and convenient movement. It has two working modes: constant temperature and intelligent temperature adjustment. The mode of intelligent temperature control can be adjusted to the corresponding water temperature as the temperature changes. Next, learn more about the issues that need to be noted during the operation of HORIZONTAL TYPE CONDENSING UNIT.
The HORIZONTAL TYPE CONDENSING UNIT used today belongs to the technical field of CNC machine tools. The structure of its refrigeration system is provided with an inlet and an upper outlet, and the oil heat exchanger is connected to the refrigeration compressor. It is arranged under the refrigerant compressor, the oil pump is arranged under the oil tank, and the inlet and the lower outlet are arranged under the oil pump. Nowadays, the new type adopts miniature high-lift oil pump with high energy efficiency ratio, in different installation methods, simple structure, easy to clean and maintain.
The HORIZONTAL TYPE CONDENSING UNIT used now includes an axial fan that is fixedly connected to the housing, where the radiator is fixedly connected to the housing, through bolts on the outside, the dust-proof network passes through the screws, and the rectangular plate is fixedly installed on the back of the radiator. The radiator has a heat sink, and now a new type of dust-proof net is installed on the back of the chiller, which effectively reduces the dust in the working environment attached to the heat sink, protects the heat sink, and extends air cooling.
When the fuel tank is in an oil-free state, the oil pump cannot run. When the oil level in the HORIZONTAL TYPE CONDENSING UNIT is relatively low, the oil pump will automatically stop working, and the oil pump indicator light will also indicate the fault indication. Add oil to ensure the normal operation of the chiller. When operating the switch, in order to ensure better normal operation of the HORIZONTAL TYPE CONDENSING UNIT, the power supply should avoid continuous switching, otherwise it is easy to cause danger to the condenser due to misoperation.