At present, as the temperature continues to rise everywhere, it is a test and suffering for PACKAGE INVOTECH SCROLL CONDENSING UNIT and us. In such a high temperature situation, some PACKAGE INVOTECH SCROLL CONDENSING UNIT will also have a series of problems. Therefore, at this time, we should do a good job of inspection and maintenance. And to master the requirements of PACKAGE INVOTECH SCROLL CONDENSING UNIT for ambient temperature. Solving this problem will be very beneficial to our maintenance of the machine.
Now many varieties of PACKAGE INVOTECH SCROLL CONDENSING UNIT are used in different production workshops or working environments. Every product has requirements for the temperature of the environment. Normally we will put PACKAGE INVOTECH SCROLL CONDENSING UNIT in different positions. If there are some units, we will often put them indoors, while another part will be placed outdoors. At this time, we have to choose an appropriate location according to the different indoor and outdoor temperatures.
For PACKAGE INVOTECH SCROLL CONDENSING UNIT indoor air-conditioning temperature requirements: the maximum normal indoor temperature value should not exceed 30 degrees Celsius. If the temperature exceeds 30 degrees Celsius and the temperature is still running, the PACKAGE INVOTECH SCROLL CONDENSING UNIT may be operating under overload conditions. The condensation temperature and exhaust temperature of the refrigeration system will rise, which may also cause the electrical protector to operate and cut off the power supply. The operating life of INVOTECH SCROLL CONDENSING UNIT has an impact.
The ambient temperature requirements of the outdoor PACKAGE INVOTECH SCROLL CONDENSING UNIT: According to national standards, the ambient temperature of the outdoor unit should be below 35 degrees Celsius. The air-conditioning unit should ensure normal operation and meet the cooling capacity and other indicators marked on the product tag. . The ambient temperature is within the range of 35 to 43 degrees Celsius, the air conditioning unit can operate, but the cooling capacity marked on its tag cannot be guaranteed. When it is already operating at full load, the condensing temperature, pressure, and exhaust temperature are quite high at this time. If the indoor unit has a large amount of heat, the electronic control protector may act, cut off the power supply, and stop running. When the outdoor temperature exceeds 43 degrees Celsius, the air-conditioning unit is in overload operation, which will cause the action of the electronic control protection device, cut off the power supply, and stop the operation. Knowing these issues, we can better operate different types of PACKAGE INVOTECH SCROLL CONDENSING UNIT.